This week we were called to a workshop specialising in competition engine rebuilds to look at both of their ceiling suspended Combat gas fired warm air heaters.
One of the heaters had a split heat exchanger and was leaking products of combustion into the workshop. This unit was disconnected from the gas supply and made safe.
The second unit had a faulty gas valve. We were able to get the unit working by re-using the gas valve from the unit we had disconnected. The unit was then re-commissioned and left working.
At CBS Complete we offer a wide range of services for all Gas, Oil and LPG fired appliances. As well as annual gas safety inspections, maintenance and repairs we offer our “CBS Protect Plans” providing complete peace of mind for our customers with a range of preventative maintenance schedules to suit all requirements and budgets.